Research Article  Open Access
Praveen Kumar Mishra, Anamika Yadav, "Combined DFT and Fuzzy Based Faulty Phase Selection and Classification in a Series Compensated Transmission Line", Modelling and Simulation in Engineering, vol. 2019, Article ID 3467050, 18 pages, 2019. https://doi.org/10.1155/2019/3467050
Combined DFT and Fuzzy Based Faulty Phase Selection and Classification in a Series Compensated Transmission Line
Abstract
The conventional distance protection scheme malfunctions sometimes in case of a fixed series capacitor compensated transmission line due to the change in relaying impedance of the protected line during faulty conditions. In order to mitigate this problem, a combined discrete Fourier transform and fuzzy (CDFTF) based algorithm has been proposed in this paper. This method has been tested on a 400 km, 735 kV series compensated transmission line network and WSCC 3machine 9bus system for all fault types using MATLAB/Simulink and PSCAD platforms, respectively. A fixed series capacitor is located at the middle of the protected line. The fundamental components of phase currents, phase voltages, and zerosequence current are fed as inputs to the proposed scheme. The fault detection, faulty phase selection, and fault classification are achieved within 1/2–1 cycle of power frequency. The proposed CDFTFbased scheme is less complex and is better than other data mining techniques which require huge training and testing time. Test results corroborate the proposed scheme reliability with wide variations in fault location, fault resistance, fault inception angle, evolving faults, compensation level, and heavy load interconnection. The results discussed in this work indicate that the proposed technique is resilient to wide variations in fault and system conditions.
1. Introduction
The primary reasons behind adoption of a series capacitor in the long transmission line include increased transmittable power, improved transient stability, voltage stability, power oscillation damping, and thereby reduced transmission and revenue losses. When the power system is subjected to a short circuit fault, it is accompanied by flow of huge fault current which may damage of the connected equipments and also create power quality problems. Therefore, accurate fault detection and classification are very crucial tasks in power system protection to restore the power supply and to improve the reliability. The installation cost of SCs is also less for 15–30% compensation as compared to installation/erection of a new line, and also it is not affected by environmental concerns [1, 2]. Distance relays used for the protection of a fixed series compensated line may experience overreach during a fault due to the involvement of the series capacitor in the fault loop, and also the distance function may fail to pick up a low fault current in the protected line. The distance relay protects 80–85% of the transmission line length, and it operates based on the impedance seen by relay location. The inclusion of a capacitor in the line either compensates or cancels a part of the transmission line inductance, which may result in a fault seen by the relay in its 1st zone although the fault has actually occurred in the 2nd or 3rd zone of protection. Similarly, a fault in the 1st zone can be perceived to be a fault in the reverse direction. For proper isolation of the faulty phase(s), correct knowledge of the faulted phase(s) is essential. Fast and reliable fault detection and classification technique is an important requirement in power transmission systems to maintain continuous power flow [3]. If the transmission line is series compensated, this task becomes more complicated.
Various schemes have been proposed earlier for fault classification in uncompensated and compensated transmission lines. These algorithms usually require measurements at one end or two ends of lines. To complement the existing methods, a sequence componentbased method is proposed in [4]. In [5], decision treebased fault classification is proposed for a transmission line compensated by a fixed series capacitor. Phase selection based on superimposed voltages and currents under balanced load is proposed in [6]. Faulty phase selection based on an integrated moving sum approach is proposed for SCTS in [7]. The authors of [8, 9] have developed fault classification algorithms using artificial neural networks (ANNs), but sometimes ANNbased approaches are subjected to underfit and overfit problems and may also stuck in a local minima. Methods based on adaptive neurofuzzy (ANFIS) for fault classification in the long transmission line have been proposed in [10, 11]. In [12–14], a support vector machine (SVM) has been used to classify the fault, but the schemes based on machine learning techniques require huge computational burden and are quite complex. In [15–18], fault classification schemes based on fuzzy logic have been presented with different feature extraction techniques such as discrete Fourier transform [15], wavelet transform [16], higher order statistics [17], and angular differences among the sequence components of the fundamental currents [18]. Fault classification technique based on probabilistic neural networks (PNNs) is discussed in [19]. In [20], the authors have conferred the effectiveness of an extreme learning machine for the protection of a long transmission line. Crosscountry faults and evolving faults have been investigated in [21]. Furthermore, hyperbolic Stransform and support vector regression method have been developed for protection of series compensated lines in [22]. In [23], an intelligent relaying scheme based on decision tree (DT) has been validated in the realtime digital simulator (RTDS). Recently, discrete wavelet transform and knearest neighbour have been used for fault detection, classification, and location estimation in a double circuit series compensated line in [24].
The main challenges in fault classification in an extrahighvoltage (EHV) series compensated transmission line are as follows:(a)The conventional distance relay employed in an EHV transmission line may maloperate during stressed conditions such as load variation, power swing, load encroachment, and system frequency variation. Also the distance relay underreaches and overreaches during highresistance fault and fault with high DC offset current.(b)Series capacitor is a popular device to increase the current carrying capacity of a transmission line by reducing the effective length of line. Change in the line current and voltage affects the seen impedance by the conventional distance relay. Moreover, it may result in voltage or current inversion and hence result in malfunction of the relay for certain types of faults [2].(c)Moreover, it is required to have two separate algorithms to deal with faults occurring before series capacitor and after series capacitor.(d)Presence of a metal oxide varistor (MOV) and bypass switches may also lead to the challenges [2] in protection of transmission lines. MOVs change the effective impedance of the installation depending on the degree of MOV conduction, which is nonlinear.
This paper aims to validate the CDFTFbased approach for classification of all the shunt faults in a series compensated system. Feasibility of the proposed CDFTFbased scheme has been tested on a 735 kV, 60 Hz, and 400 km long transmission system and a modified WSCC 3machine 9bus system which is a midpointfixed series capacitor compensated in MATLAB/Simulink [25]and EMTDC/PSCAD platforms, respectively. The main novelty of the proposed work can be explained as follows:(a)The proposed scheme is very simple and easy to implement as it uses the fundamental phasor of the signals at one end only and then it applies the Fuzzy approach to make the final decision.(b)In the proposed scheme, one single Fuzzybased relay can detect and classify the fault either before or after the series capacitor, whereas in the existing scheme two separate algorithms are required.(c)There is no requirement of a communication channel between two ends and hence the reliability is improved, and furthermore cost and computation burden is reduced.(d)The speed of the presented relaying scheme is within half cycle of power frequency (i.e., less than 10 ms).(e)The proposed scheme works well for an evolving fault and heavy load interconnection.(f)Efficacy of the proposed scheme is also validated on a modified WSCC 3machine 9bus series compensated network and provides an average accuracy of 99.678%.
The paper is divided into six sections. Section 2 gives a brief overview of the series compensated transmission system. In section 3, the CDFTFbased scheme is discussed. In section 4, it illustrates the performance of the proposed algorithm under different fault scenarios. In section 5, it compares the proposed with earlier reported schemes. In the final section, the concluding remarks have been given.
2. Series Compensated Transmission System (SCTS)
The singleline diagram of 735 kV, 60 Hz SCTS is shown in Figure 1. It consists of a doublyfed series compensated transmission system wherein source 1 is a power plant consisting of six 350 MVA generators and source 2 is a Thevenin equivalent source of the interconnected grid. The line 1 between bus B3 and bus B2 has 100 km length while the line between bus B4 and B2 has 300 km length. Further to enhance the power transmission capability of the system, the 300 km line 2 between buses B4 and B2 is the midpoint compensated by a fixed series capacitor of 62.8 µF in each phase representing 40% compensation of the reactance of line 2.
The SC is protected by the MOV block which consists of 60 columns, and its protection level is set to 238.9 kV. This voltage corresponds to 2.5 times the nominal capacitor voltage. All fault simulation studies have been carried out using the MATLAB/Simulink platform [25]. SC is protected by MOV overvoltage and the air gap. For simulation studies, a sampling frequency of 1.2 kHz is chosen. Figure 1 shows a schematic diagram of the simulated system. The system parameters are given in Appendix A.
3. Proposed CDFTFBased Fault Classification Scheme
In this work, combined DFT and fuzzy logic technique based on the fault classification scheme has been proposed for a series compensated transmission system. Figure 2 presents the flow chart of the proposed CDFTFbased technique. The fundamental component magnitude of 3phase voltages and currents are obtained after preprocessing the singleend measurements. In the preprocessing stage, the 3phase time domain (instantaneous) voltage and current signals are converted into discrete samples through zeroorder hold block with a sampling frequency of 1.2 kHz and passed through a 2ndorder low pass Butterworth filter with a band pass edge frequency of 2 ∗ pi ∗ 400 rad/s. Furthermore, the filtered discrete 3phase signals are passed through the recursive discrete Fourier transform (DFT) block available in MATLAB/Simulink to obtain the fundamental components of voltages and currents in the time domain. For knowledge of the ground involvement in the fault, a sequence analyzer is used to calculate the magnitude of zerosequence current.
After preprocessing, the fundamental component magnitude of 3phase currents and voltage signals are applied to the proposed fuzzybased fault classification algorithm. Fuzzy logic is an extension of multivalued logic and problem solution methodology which gives a better and precise conclusion from vague and imprecise data. Basically, fuzzy logic has four stages: (i) fuzzification; (ii) inference system; (iii) fuzzy rule base/knowledge base; and (iv) defuzzification. In fuzzification, crisp inputs are converted into fuzzified inputs, which are processed by the inference system according to the rules defined in the rule base/knowledge base. The decision taken by the inference system is fuzzy in nature which cannot be understood by the realtime system, so this is mapped into crisp output through the defuzzification stage. The membership function shape is very important with respect to the performance of the whole system. In this work, the triangular membership functions for fuzzification and the centroid method for defuzzification have been chosen. Figure 2 presents the flow chart of the proposed CDFTFbased technique.
During the fault in the forward direction, only fuzzybased fault classifier is activated which determines the types of faults along with the phase(s) involved. Inputs for the FFC are the magnitudes of fundamental voltage and current. The fuzzy based fault classifier (FFC) is designed separately for each phase and also for ground identification.
Based on the type of fault that has occurred in the line, corresponding faulted phase(s) and ground output become high (1) and healthy phase(s) output remains low (1). Thus, both the faulty phase(s) and the type of fault are identified using the proposed scheme as exemplified in Figure 2. About the ground involvement, the magnitude of zerosequence current is taken. For identification and classification of faulty phase(s), the fundamental component of voltage and current using DFT is considered as input. The zerosequence current signal is obtained using the sequence analyzer in order to determine the ground involvement.
Steps to design the fuzzy rules are as follows:(a)Simulate all ten types of faults in the MATLAB/Simulink model of the test system at 10 km and 290 km from the relaying bus with the variation in fault resistance (i.e., 10 Ω and 100 Ω) and fault inception angle (0, 45, 90, and 270).(b)Obtain the fundamental components of voltage and current signals using the fullcycle DFT algorithm and also estimate the zerosequence current signal.(c)After observing the behaviour of voltage and current signals for all simulated cases as discussed in step (a), categorize the voltage and current signals into three ranges such as V_{LOW}, V_{MED}, and V_{HIGH} and I_{LOW}, I_{MED}, and I_{HIGH}, respectively. And also to know the ground involvement in fault conditions, subcategorize zerosequence current into the three ranges I_{LOW}, I_{MED}, and I_{HIGH}.(d)Design the fuzzy rule base and ranges of membership functions as depicted in Tables 1 and 2.


Each voltage and current signal is divided into three ranges with triangular membership function (TMF): low, medium, and high, as described in Table 2. FFC provides four outputs corresponding to the three phases, namely, “phase A,” “phase B,” “phase C,” and “ground G” which goes high (1) in the case of fault occurrence or else remains low (0) during healthy conditions. Output trip logic also consists of two ranges, namely, trip low TL (0) and trip high TH (1). The effect of variations on different fault factors has also been studied, such as fault type, fault location, fault resistance, fault inception angle, evolving fault, compensation level, etc.
As illustrated in Figure 2, if a fault occurs in the protected zone, threephase voltage and current signals are acquired at the relay point which will be further preprocessed by fullcycle DFT for the feature extraction process. The sampling frequency for the collected signal is kept to be 1.2 kHz. To know the ground involvement, the zerosequence component of the current signal has been calculated. Extracted features of voltage and current signals, i.e., fundamental components, are fed to the fuzzy module of phase(s). FFC deliver the four outputs A, B, C, and G which are declared as “zero” in the case of “no fault” and otherwise “one.”
If A = B = C = G = 1, then FT is ABCG fault; if A = B = G = 1 and C = 0, then FT is ABG fault; if A = B = 1 and C = G = 0, then FT is AB fault; if A = G = 1 and B = C = 0, then FT is AG fault.
In this paper, we have used TMF as shown in Figure 3 which is specified by three parameters {P, Q, R} whose values have been taken as described in Table 2 for phase(s) as well as for ground detection and classification. The rule base designed for ground detection is as follows:(i)If zerosequence current is I_{LOW} or I_{MID}, then the trip is TL(ii)If zerosequence current is I_{HIGH}, then the trip is TH
Detection and classification time of the relay for faulty phase(s) can be calculated as follows:where , , and stand for the response time taken by the relay to classify the faults, the relay operating time, and the time of inception of a fault, respectively. From Table 3, it is clear that the time taken to classify phase(s) and ground is less than half cycle in almost all of the fault cases. The SCTS has been simulated using MATLAB/Simulink software.

The aim of this study is to validate various fault circumstances, and a huge fault dataset has been considered with wide variations in fault parameters, such as fault location (FL), fault resistance (FR), fault inception angle (FIA), and fault type (FT) under wide variations in system conditions. The different system conditions have been generated with various compensation levels. The values of the fault parameters considered in this paper are as follows:(i)Fault location (FL): 20 number of random locations(ii)Fault resistance (FR): 0.001, 10, 20, 30, 40, 50, 60, 80, and 100 Ω(iii)Fault inception angle (FIA): 0°, 45°, 90°, 135°, 180°, 225°, 270°, 315°, and 360°(iv)Fault type (FT): all 10 types (LG, LLG, LL, and LLL)(v)Level of compensation (%X): uncompensated, 10, 20, 30, 40, 50, 60, and 65% for FIA = 0°
Therefore, a total of 129600 fault cases has been generated [(FL ∗ 20) ∗ (FR ∗ 9) ∗ (FIA ∗ 9) ∗ (FT ∗ 10) ∗ (%Xc ∗ 8)].
4. Performance Evaluation of the Proposed Scheme
To evaluate the effectiveness of the CDFTFbased scheme, a 735 kV, 60 Hz 3phase series compensated transmission system (SCTS) with a distributed line model as shown in Figure 1 has been considered and simulated in the MATLAB/Simulink environment. The system details have been provided in Appendix A. During normal system condition, power flow takes place from Bus B1B2. The voltage and current signals are acquired at the relaying point, i.e., at Bus B4. The sampling rate for the collection of voltage and current signals is maintained at 1.2 kHz.
4.1. Effect of Fault Location
The effect of variations in the fault location on the performance of the presented scheme has been analyzed with varying resistance in the range of 0.001 Ω to 50 Ω for all shunt faults. Test results of the variations in fault locations are summarized in Table 4. Figures 4(a) and 4(b) show the time domain signals of 3phase voltage and current during the AB fault occurred at 135 km from the relaying point with FR = 10 Ω, FIA = 0° at 0.5 sec. Figure 4(c) shows the performance of the classification module in which phases A and B rise up (1) both at 0.5042 sec. Phase C and ground G remain low (0) after the inception of the fault at 0.5 sec. So, the proposed scheme provides better protection, covering 90% of the line length.

(a)
(b)
(c)
4.2. Effect of Fault Resistance
Another parameter that might have an impact on fault classification is fault resistance because, in the case of faults involving ground, FR may cause incorrect operation of the conventional distance relay. The impacts of this parameter on the proposed scheme have been studied with variations in fault resistance. Test results during variations of FR on the presented CDFTFbased technique are shown in Table 5. The proposed method has been proved to be effective in classifying the fault type with variations in fault resistance ranging from 0.001 Ω to 100 Ω. Figures 5(a) and 5(b) show the input to FFC 3phase time domain voltage and current signals. Figure 5(c) presents the performance of FFC output. In Figure 5, LLG (ABG)type fault occurred in protected SCTS with FR = 40 Ω and FIA = 45° at FL = 205 km is shown. The output of FFC shows that phases A and B and ground G go high (1) at 0.5067 sec, 0.5108 sec, and 0.5083 sec, respectively, after the inception of the fault at 0.5025 sec with phase C remaining low (0) and unchanged, confirming the nature of ABG fault. Table 5 summarizes the performance of the proposed scheme, which presents the time required to classify the fault(s) that is considerably less than half cycle of power frequency in most of the cases.

(a)
(b)
(c)
4.3. Effect of Fault Inception Angle
Faults in a transmission line can occur at any time instant. So, the proposed CDFTFbased method has also been tested for varying FIA, and results have been presented in Table 6. For all the tested cases, the response time for classification of faults is within one cycle of power frequency in most of the cases. Fault classification inputs and outputs during ABCtype LLL fault including FIA = 180° at 175 km from the relaying point are shown in Figure 6. 3phase sinusoidal voltages and currents are shown in Figures 6(a) and 6(b), respectively. Figure 6(c) shows the outputs of FFC where all the three faulty phases A, B, and C become high (1) after 0.5167 sec and ground output G remains low (0) all the time.

(a)
(b)
(c)
4.4. Effect of Fault Type
The proposed CDFTFbased method also helps in identifying and classifying the faulty phase(s) with the variation in shunt fault types. Basically, there are 10 fault types that involve all combinations of A, B, C, and G. All FT must be applied to test the ability of the relay for accurate classification of the faulty phase(s). Some of the results are tabulated in Table 7. The response time of the presented CDFTFbased relay with wide variations in fault types is included in Table 7.

Figures 7(a) and 7(b) show the graphical time domain 3phase voltage and current signals at relaying bus B4 for an AG fault including FIA = 45° and FR = 50 Ω at 50 km. Figure 7(c) shows the output of FFC in which phase A and ground G go high (1) at 0.5058 sec and 0.5050 sec, respectively, and all other phases remain low (0), clearly indicating the occurrence of AG fault. Hence, it can be inferred that the proposed technique is capable of classifying faults in less than half cycle in most of the cases.
(a)
(b)
(c)
4.5. Effect of Evolving Faults
The effectiveness of the proposed CDFTFbased technique has been examined for evolving faults. An evolving fault can be defined as a fault where the involvement of phases changes over a period of time. For example, an evolving fault begins as a single linetoground fault, and after a short time interval, it transforms into a double linetoground fault [21]. The characteristic of an evolving fault is that its faulted phases change over time, while other types of faults’ faulted phases remain unchanged. The effectiveness of the presented scheme during evolving faults has been examined, and some of the results are presented in Table 8. From Table 8, it can prove that the proposed CDFTFbased method can classify the evolving faults correctly within half cycle in most of the conditions. Figures 8(a) and 8(b) present the threephase time domain voltage and current signal, and the output of FFC is presented in Figure 8(c). Single line to ground (BG) has been considered initially with FR of 15 Ω and fault inception time being 0.51 sec at 90 km from relaying bus B4. This BG fault is transformed into double linetoground fault (BCG) with FR of 50 Ω just after the initiation of an initial fault. The time deviations between the two faults are 26 ms. In Figure 8(c), it is clearly examined that the faulty phases B and C and ground G become high (1) after fault inception with phase A remaining low (0). Proposed schemes correctly classify the faulty phase(s) within a cycle.
 
FT1, initial fault types; FT2, secondary fault types; FR1, initial fault resistance; FR2, secondary fault resistance; IT1, inception time for the initial fault type; IT2, inception time for the secondary fault type. 
(a)
(b)
(c)
4.6. Effect of Level of Compensation
Most of the schemes which have been reported in the literature are basically designed for a specific compensation level; as the compensation level increases or decreases, the performance of schemes may get affected, and also at higher compensation levels, the SSR (subsynchronous resonance) phenomenon is predominant. To know the feasibility of the proposed scheme with the wide variations in the level of compensation level (from %Xc = 10%–80%), various simulation studies have been performed. Table 9 summarizes the results of the simulation studies.

The 3phase voltage and current signals are shown in Figures 9(a) and 9(b) for a DLGF (double linetoground fault) in phases B and C with an FR of 10 Ω and FIA of 0° at 165 km from relaying bus B4. The outputs of the fault classification network are shown in Figure 9(c), wherein phases B and C and ground (G) become high (1) after 3.3 ms, with phase A remaining low (0) all the time.
(a)
(b)
(c)
The results approve the accurate effectiveness of the proposed technique under wide variations in the compensation level. The proposed scheme gives a good result for the classification of faults and faulty phase(s).
4.7. Effect of Change in System Frequency
In the literature survey, we found that authors have not been discussed the performance of their schemes under wide variations in system frequency. System frequency matters a lot in the protection of an electrical power system network. Various power system components such as induction machine, transformers, generators, and their operations depend on the frequency of the electrical system. Also, the stability of the power system relies on the frequency of the system. If frequency deviation between the source end and the load end is more, then there is a probability of generators falling out of synchronism. To test the feasibility of the proposed method for the change in system frequency, consider fault type is DLGF in phases A and B with FR of 20 Ω and FIA of 0° at 170 km from relaying point B4 with wide variations in system frequency. Results are illustrated in Table 10.

Consider fault type is a double linetoground fault in phases A and B with an FR of 20 Ω and FIA of 0° at 170 km from relaying bus B4. The behaviour of voltage, current, and the proposed scheme during the ABG fault is shown in Figure 10.
(a)
(b)
(c)
Figure 10(c) shows that the outputs of the fault classification network wherein phases A and B and ground G become high after 4.2 ms, 3.5 ms, and 6.4 ms respectively, and phase C is low all the time. Results approve the accurate performance of the proposed method under wide variations in system frequency. The proposed scheme gives a good result for the classification of fault and faulty phase(s) within 7 ms.
4.8. Effect of Heavy Load Interconnection
Performance of the presented CDFTFbased technique has also been investigated for heavy load condition. Nature of the load is probabilistic in the distribution side. Sometimes, the relay considers sudden change in the load on bus as a fault. The relay may maloperate, and the healthy part of the system might be removed, which creates nonreliability of power and causes revenue losses. In order to investigate the effect of heavy load interconnection on the effectiveness of the proposed scheme, a variety of simulations has been carried out, considering wide variations in system frequency. Some of the simulation results are presented in Table 11.

Consider the load of P = 1000 MW and Q = 800 MVAr is inserted on bus B2 in Figure 1, and the switching instant of load to bus B2 is 0.5 sec at the system frequency of 60 Hz. Fault classification outputs during this heavy load interconnection are shown in Figures 11(a) and 11(b), respectively. Figures 11(a) and 11(b) show 3phase voltage and current waveform, and Figure 11(c) presents the output of FFC wherein all the phases, i.e. A, B, and C, and ground G is low (0) all the time. The results approve that performance of the proposed scheme is perfect with varying system frequency.
(a)
(b)
(c)
5. Validation of the Proposed Scheme Using EMTDC/PSCAD
In order to test the proposed CDFTFbased scheme with more realistic system conditions, different fault situations have been simulated in the modified WSCC 3machine 9bus system [26] using EMTDC/PSCAD software. The system parameters are given in Appendix B. The singleline diagram of the modified WSCC 9bus system is shown in Figure 12. The relay is placed near to bus 7, so the transmission line between bus 7 and bus 8 is considered to be protected which is 40% series compensated by a fixed series capacitor. Different fault situations have been simulated by varying fault parameters such as fault type (LG, LLG, LL, and LLL), fault location (10–390 km with a step of 10 km), fault inception angle (0°–315° with a step of 45°), and fault resistance (0–100 Ω with a step of 20 Ω). The fault signals generated from PSCAD software are preprocessed using MATLAB/Simulink software to obtain fundamental component values of voltage and current signals and then used as input to the fuzzy logicbased classifier:
The fault classification modules correctly identify the involvement of phase(s) and ground. For instance, CA fault is created at 160 km, FIA = 90°, FR = 0.001 Ω, and %Xc = 40%; in this case, the threephase voltage and current signals obtained from PSCAD software simulation are shown in Figures 13(a) and 13(b), and output of the fuzzy fault classifier is shown in Figure 13(c). Figure 13(c) shows the performance of the classification module in which phases A and C rise up (1) both at 3 ms and 5 ms, respectively, while phase B and ground G remain low (0) after the inception of the fault at 2.005 sec. Some of the test results are presented in Table 12. Analyzing the results of Table 12, it is concluded that the proposed method has an accurate and reliable performance in various system conditions in the modified WSCC 3machine 9bus system.
(a)
(b)
(c)

For investigating the robustness of the proposed scheme, different faults are simulated in different conditions by varying different fault parameters. Total fault cases simulated are 5 (RF value) × 32 (fault locations) × 8 (FIA) × 10 (fault type) + 20 = 12820 cases. All these test cases have been applied to the proposed scheme, and the fault classification accuracy and correctness are measured in terms of the confusion matrix and presented in Table 13. The confusion matrix is a very concrete method to measure of robustness and accuracy of the proposed scheme. It can be observed from the confusion matrix that all the cases are predicted by the proposed scheme with an average accuracy of 99.678%. The result confirms that the proposed CDFTFbased scheme works correctly for the EMTDC/PSCAD fault simulation also.

6. Comparisons with Other Schemes
A summarized result of the comparative performance evaluation of the proposed CDFTFbased scheme with some other classification methods available in the literature is shown in Table 14. Most of the schemes reported in Table 14 have not discussed regarding the evolving fault, change in the system frequency, and heavy load interconnection. In most of the cases, the proposed schemes take half cycle time to classify the faults and the accuracy is about 100% compared to all other methods shown in Table 14. It can be observed that the time required by the proposed CDFTFbased scheme to classify the fault is 1/2–1 cycle. In addition, the proposed scheme is robust to wide variations in fault parameters, and moreover the scheme works well for evolving fault classification also. Furthermore, the performance is not affected by change in frequency and heavy load interconnection which have not been considered by earlier reported techniques.

7. Conclusion
This article presents a combined discrete Fourier transform and fuzzy logic based relaying scheme for protection of the series compensated transmission line. The process is started at retrieving the current and voltage signal features and preprocessing through discrete Fourier transform to obtain the fundamental component of voltage and current. The voltage and current features are used to build the fuzzy rule base for detection and classification of faults. The speed of the presented relaying technique is within half cycle of power frequency. Regarding fault detection and classification, the algorithm is capable of detecting and classifying all types of faults under varying fault and system conditions. Also, the variation in fault location, fault resistance, system frequency, and evolving fault do not affect the classification process. The CDFTFbased fault classification scheme has proved to be reliable, fast, and accurate against different fault situations in different series compensated transmission systems.
Appendix
A. System Parameter Details of Network Shown in Figure 1
The parameters of each line are as follows:
Line 1: 100 km
Line 2: 300 km
Positive sequence impedance = 0.01273 + j0.35199 Ω/km
Positive sequence capacitance = 0.01274 µF/km
Zerosequence impedance = 0.3864 + j1.5556 Ω/km
Zerosequence capacitance = 0.007751 µF/km
Compensation level: 40%
MOV voltage rating: 298.7 kV, 30 MJ
Parameters of each source are as follows:
Source 1: 6 ∗ 350 MVA, 13.8 kV, 60 Hz, %X = 22
Source 2: 30000 MVA, 735 kV, 60 Hz
Parameters of each transformer are as follows:
Transformer 1: 350 MVA, 13.8/735 kV, 60 HZ, %X = 8%
Transformer 2: 300 MVA, 735/230 kV, 60 Hz, %X =15%
Parameters of each load are as follows:
Load 1: P = 100 MW
Load 2: P = 132 MW, Q = 330 MVAr
Load 3: P = 132 MW, Q = 330 MVAr
Load 4: P = 250 MW
B. System Parameter Details of Network Shown in Figure 12
System data for WSCC 3machine 9bus configuration:
Generator:
Gen 1: 600 MVA, 22 kV, 50 Hz; Gen 2: 465 MVA, 22 kV, 50 Hz; Gen 3: 310 MVA, 22 kV, 50 Hz
X_{d} = 1.81 p.u., X′_{d} = 0.3 p.u., X″_{d} = 0.23 p.u., T′_{d0} = 8 s, T″_{d0} = 0.03 s, X_{q} = 1.76 p.u., X″_{q} = 0.25 p.u., T″_{q0} = 0.03 s., R_{a} = 0.003 p.u., X_{p} (Potier reactance) = 0.15 p.u.
Transformer:
T1: 600 MVA, 22/400 kV, 50 Hz, ∆/Y
T2: 465 MVA, 22/400 kV, 50 Hz, ∆/Y
T3: 310 MVA, 22/400 kV, 50 Hz, ∆/Y
X = 0.163 p.u., X_{core} = 0.33 p.u., R_{core} = 0.0 p.u., P_{copper} = 0.00177 p.u.
Transmission line:
Length of line 78 = 320 km, line 89 = 400 km, line 75 = 310 km, line 54 = 350 km, line 64 = 350 km, line 6–9 = 300 km
Positive sequence impedance = 0.12 + j0.88 Ω/km
Zerosequence impedance = 0.309 + j 1.297 Ω/km
Positive capacitive reactance = 487.723 × 10^{3} Ω/km
Zerosequence capacitive reactance = 419.34 × 10^{3} Ω/km
Loads:
Load A = 300 MW + j 100 MVAr
Load B = 200 MW + j 75 MVAr
Load C = 150 MW + j 75 MVAr
Data Availability
The data used to support the findings of this study are available from the corresponding author upon request.
Conflicts of Interest
The authors declare that they have no conflicts of interest.
References
 B. Vyas, R. P. Maheshwari, and B. Das, “Protection of series compensated transmission line: issues and state of art,” Electric Power Systems Research, vol. 107, no. 1, pp. 93–108, 2014. View at: Publisher Site  Google Scholar
 P. M. Anderson, Power System Protection, IEEE Press, New York, NY, USA, 1999.
 A. G. Phadke and J. S. Thorp, Computer Relaying for Power Systems, John Wiley & Sons, Chichester, UK, 1988.
 T. Adu, “An accurate fault classification technique for power system monitoring devices,” IEEE Transactions on Power Delivery, vol. 17, no. 3, pp. 684–690, 2002. View at: Publisher Site  Google Scholar
 U. B. Parikh, B. R. Bhalja Jr., R. P. Maheshwari, and B. Das, “Decision tree based fault classification scheme for protection of series compensated transmission lines,” International Journal of Emerging Electric Power Systems, vol. 8, no. 6, 2007. View at: Publisher Site  Google Scholar
 D. W. P. Thomas, M. S. Jones, and C. Christopoulos, “Phase selection based on superimposed components,” IEE ProceedingsGeneration, Transmission and Distribution, vol. 143, no. 3, pp. 295–299, 1996. View at: Publisher Site  Google Scholar
 M. Biswal, “Faulty phase selection for transmission line using integrated moving sum approach,” IET Science, Measurement & Technology, vol. 10, no. 7, pp. 761–767, 2016. View at: Publisher Site  Google Scholar
 B. Y. Vyas, B. Das, and R. P. Maheshwari, “Improved fault classification in series compensated transmission line: comparative evaluation of Chebyshev neural network training algorithms,” IEEE Transactions on Neural Networks and Learning Systems, vol. 27, no. 8, pp. 1631–1642, 2016. View at: Publisher Site  Google Scholar
 J. Upendar, C. P. Gupta, G. K. Singh, and G. Ramakrishna, “PSO and ANNbased fault classification for protective relaying,” IET Generation, Transmission & Distribution, vol. 4, no. 10, pp. 1197–1212, 2010. View at: Publisher Site  Google Scholar
 H. Eristi, “Fault diagnosis system for series compensated transmission line based on wavelet transform and adaptive neurofuzzy inference system,” Measurement, vol. 46, no. 1, pp. 393–401, 2013. View at: Publisher Site  Google Scholar
 P. K. Dash, A. K. Pradhan, and G. Panda, “A novel fuzzy neural network based distance relaying scheme,” IEEE Transactions on Power Delivery, vol. 15, no. 3, pp. 902–907, 2000. View at: Publisher Site  Google Scholar
 P. K. Dash, S. R. Samantaray, and G. Panda, “Fault classification and section identification of an advanced seriescompensated transmission line using support vector machine,” IEEE Transactions on Power Delivery, vol. 22, no. 1, pp. 67–73, 2007. View at: Publisher Site  Google Scholar
 U. B. Parikh, B. Das, and R. Maheshwari, “Fault classification technique for series compensated transmission line using support vector machine,” International Journal of Electrical Power & Energy Systems, vol. 32, no. 6, pp. 629–636, 2010. View at: Publisher Site  Google Scholar
 U. B. Parikh, B. Biswarup Das, and R. P. Prakash Maheshwari, “Combined waveletSVM technique for fault zone detection in a series compensated transmission line,” IEEE Transactions on Power Delivery, vol. 23, no. 4, pp. 1789–1794, 2008. View at: Publisher Site  Google Scholar
 A. Yadav and A. Swetapadma, “Enhancing the performance of transmission line directional relaying, fault classification and fault location schemes using fuzzy inference system,” IET Generation, Transmission & Distribution, vol. 9, no. 6, pp. 580–591, 2015. View at: Publisher Site  Google Scholar
 A. K. Pradhan, A. Routray, S. Pati, and D. K. Pradhan, “Wavelet fuzzy combined approach for fault classification of a seriescompensated transmission line,” IEEE Transactions on Power Delivery, vol. 19, no. 4, pp. 1612–1618, 2004. View at: Publisher Site  Google Scholar
 A. K. Pradhan, A. Routray, and B. Biswal, “Higher order statisticsfuzzy integrated scheme for fault classification of a seriescompensated transmission line,” IEEE Transactions on Power Delivery, vol. 19, no. 2, pp. 891–893, 2004. View at: Publisher Site  Google Scholar
 B. Das and J. V. Reddy, “Fuzzylogicbased fault classification scheme for digital distance protection,” IEEE Transactions on Power Delivery, vol. 20, no. 2, pp. 609–616, 2005. View at: Publisher Site  Google Scholar
 S. R. Samantaray and P. K. Dash, “Pattern recognition based digital relaying for advanced series compensated line,” International Journal of Electrical Power & Energy Systems, vol. 30, no. 2, pp. 102–112, 2008. View at: Publisher Site  Google Scholar
 V. Malathi, N. S. Marimuthu, S. Baskar, and K. Ramar, “Application of extreme learning machine for series compensated transmission line protection,” Engineering Applications of Artificial Intelligence, vol. 24, no. 5, pp. 880–887, 2011. View at: Publisher Site  Google Scholar
 A. Swetapadma and A. Yadav, “All shunt fault location including crosscountry and evolving faults in transmission lines without fault type classification,” Electric Power Systems Research, vol. 123, pp. 1–12, 2015. View at: Publisher Site  Google Scholar
 Z. Moravej, M. Khederzadeh, and M. Pazoki, “New combined method for fault detection, classification, and location in seriescompensated transmission line,” Electric Power Components and Systems, vol. 40, no. 9, pp. 1050–1071, 2012. View at: Publisher Site  Google Scholar
 M. K. Jena and S. R. Samantaray, “Intelligent relaying scheme for seriescompensated double circuit lines using phase angle of differential impedance,” International Journal of Electrical Power & Energy Systems, vol. 70, pp. 17–26, 2015. View at: Publisher Site  Google Scholar
 A. Swetapadma, P. Mishra, A. Yadav, and A. Y. Abdelaziz, “A nonunit protection scheme for double circuit series capacitor compensated transmission lines,” Electric Power Systems Research, vol. 148, pp. 311–325, 2017. View at: Publisher Site  Google Scholar
 MATLAB, Version R2013a, The MathWorks Inc., Natick, MA, USA.
 P. K. Nayak, A. K. Pradhan, and P. Bajpai, “A fault detection technique for the seriescompensated line during power swing,” IEEE Transactions on Power Delivery, vol. 28, no. 2, pp. 714–722, 2013. View at: Publisher Site  Google Scholar
Copyright
Copyright © 2019 Praveen Kumar Mishra and Anamika Yadav. This is an open access article distributed under the Creative Commons Attribution License, which permits unrestricted use, distribution, and reproduction in any medium, provided the original work is properly cited.